OUR1 Timer, Using for timing and one shot
|Welcome Guest ( Log In | Register )|
Nov 2 2011, 05:17 PM
Joined: 27-October 11
Member No.: 12,835
I have a control panel that controls multiple pieces of equipement. Currently there are 3 remote start buttons (momentary) that activate a 480v contact set with hold. I have been asked to install an alarm bell that will ring for 3-5 seconds when the start button is pressed before the equipement will start. I have been looking at the side of this timer (OUR1) and am not understanding exactly how it would operate. Could you guide me to a more detailed explanation of the diagrams or suggest a timer that would do that for me.
Nov 7 2011, 05:23 PM
Group: Authorized Member
Joined: 26-June 09
Member No.: 6,956
Based on your requirement I think that you have to use function B (Single Shot). Here you can find a description of this function, among other common timing functions: Quick Tip - Timing Functions - Part 1.pdf
Your contact will have to supply line voltage to the Y1 terminal on the timer, which is the control terminal.
The only problem that I see is that this timer has an operating voltage of 24 VDC or 24 to 240 VAC. We don't have any timer that will take 480 VAC, so you will have to get a lower voltage from somewhere in your system.
Time is now: 25th April 2014 - 03:23 AM